BWU3785Active Distributor ASi, IP67, 3I/4O
Active Distributor ASi, IP67, housing depth 35 mm, 3 digital inputs, 4 digital outputs, input voltage/sensor supply out of AUX, output voltage/actuator supply out of AUX, periphery connection via 2 x M12 cable sockets, straight, 5 poles, cable lengths: 1 x 0,25 m and 1 x 2 m, flat design, installation in cable duct possible (installation depth > 35 mm), LED, connections for 1 x ASi profile cable and 1 x AUX profile cable, ASi connection via profile cable and piercing technology, 1 AB address
|Outputs digital||4 x electronic|
Input voltage (sensor supply)
inputs are supplied by ASi or by AUX (auxiliary 24 V power). If supplied by ASi, inputs shall not be connected to earth or to external potential.
|out of AUX|
Output voltage (actuator supply)
Electronic outputs are supplied by ASi or by AUX (auxiliary 24 V power). If supplied by ASi, outputs shall not be connected to earth or to external potential.
For relay outputs the relay contacts are initiated from ASi. The load circuit is powered externally as specified in the data sheet.
|out of AUX|
|Connection||2 x M12 cable sockets, straight, 5 poles|
Under normal conditions (no bus termination or repeater), the permissible total length of the ASi segment is max. 100 m. The calculation should take into consideration that the length of the connection cable (round cable) for each connected passive distributor must be doubled.
In the case of the active distributors (ASi modules) however only the one ASi profile cable is counted.
|X1: 0,25 m, X2: 2 m|
AB address (max. 62 AB addresses/ASi network), 2 AB addresses (max. 31 modules with 2 AB addresses), Single addresses (max. 31 Single addresses/ASi network), ASi-5 address (max. 62 ASi-5 addresses/ASi network), mixed use allowed.
|1 AB address|
How to get started with Bihl+Wiedemann products
How to easily implement your ASi installation
How to troubleshoot an existing ASi installation
Quick Start Guides
- Quick Start Guide: Tips & Tricks: Replacing a defective device (DE)
- Quick Start Guide: Tips & Tricks: Replacing a defective device (EN)
- Quick Start Guide: ASIMON360 Configuration of Safety devices (DE)
- Quick Start Guide: ASIMON360 Configuration of Safety devices (EN)
- Quick Start Guide: ASIMON360 Configuration of Safety devices (PL)
Magnetic holders for substructure Modules» show product details
ASi-5/ASi-3 Address Programming Device» show product details